The Universal Security Instruments USI-3204 Battery-Operated Photoelectric Smoke and Fire Alarm responds especially fast to slow-smoldering fires. Perfect for new or replacement installations, the 120-volt AC hardwired alarm is suitable for houses, apartments and mobile homes. The 9-volt battery (included) provides continuous protection in the event of a power outage. Ideal for replacement of existing smoke alarms, this alarm features a large mounting plate for coverage of drywall impressions or old paint marks. The red LED light flashes when smoke is detected and the green LED light indicates that the power is functioning.
Full dust and contaminant covers protect the device from spray applications, so you will not need to remove the alarm during any construction procedures. This smoke and fire alarm is UL Listed, California State Fire Marshal approved and Federal Housing Authority (FHA) approved to exceed industry standards. For maximum protection, install an alarm inside every bedroom, outside every sleeping area and on all levels of the dwelling.
The USI Electric USI-3204 Battery-Operated Photoelectric Smoke and Fire Alarm comes with a 5 year limited warranty. USI Electric is a subsidiary of Universal Security Instruments Inc., a U.S. based manufacturer of high quality, easy-to-install home safety products. Founded in 1969, Universal Security Instruments has over 40 years of heritage in providing home safety products for families. With state-of-the-art manufacturing facilities, Universal Security Instruments continues to launch revolutionary new products and technologies with the mission of always working to keep families protected.
Q: WHY DOES MY SMOKE ALARM 'CHIRP' APPROXIMATELY ONCE EVERY MINUTE?
A: The smoke alarm chirps to indicate a "low battery" condition, meaning the battery needs to be replaced. Battery powered smoke alarms will chirp a minimum of 30 days before the battery completely loses power.
AC powered smoke alarms with battery backup will chirp indefinitely assuming AC power is present; if battery power is low, or battery is removed; until a fresh battery is installed. Approved replacement batteries are listed on the back of each smoke alarm and in the user's manual.
Certain model smoke alarms with a silence button (designed to silence the alarm during a nuisance alarm) may chirp to indicate the smoke alarm is in the silence mode. The chirp will stop after approximately 8 minutes and the smoke alarm will return to its normal operation.
Q: WHAT DOES IT MEAN WHEN THE RED LIGHT ON THE ALARM FLASHES APPROXIMATELY ONCE EVERY MINUTE?
A: The flashing red light gives a visual indication that the smoke detector is functioning properly. It also indicates a working battery is connected to the smoke alarm.
Q: WHAT DOES THE CONTINUOUS GREEN LIGHT ON MY SMOKE ALARM INDICATE?
A: When a green light is present on your smoke detector, it means that AC power is currently operating the alarm.
Q: THE GREEN LIGHT ON MY SMOKE ALARM HAS GONE OUT, WHAT DOES THIS MEAN?
A: If the green light on your smoke detector is not on, it means the AC power has been interrupted to the alarm. Check the circuit breaker and AC wiring to make sure power is still reaching the smoke alarm.
Q: HOW CAN I TELL WHICH SMOKE ALARM IN A MULTI-STATION SYSTEM INITIATED THE ALARM?
A: When interconnected alarms are alarming, the smoke alarm which initiated the alarm, either by test button or sensing smoke, will flash the red LED light approximately once per second. The red LED light on the other non-initiated interconnected smoke detectors will not be lit but will sound the alarm.
Q: HOW MANY SMOKE ALARMS OR DEVICES CAN BE INTERCONNECT AT ONE TIME?
A: The NFPA 72 standard states the interconnect limit is 12 smoke alarms and up to 6 other alarms (heat alarms or carbon monoxide detectors) for a total of 18 total alarms. With 18 alarms interconnected, up to an additional 6 relay modules may be interconnected (for a maximum of 24 devices).
If battery backup alarms and non-battery backup alarms and accessories are mixed in an interconnect system, all devices without battery backup WILL NOT operate during an AC power failure.
CAUTION: USI alarms and accessories should only be interconnected with other USI alarms and accessories. Connecting devices from another manufacturer to USI devices may result in nuisance alarms, failure to alarm, or damage to one or all of the devices in the interconnect system. All interconnected USI alarms should be powered by the same fuse or circuit breaker. Smoke alarms shall not receive their power from a circuit that is protected by a ground fault circuit interrupter. Improper connection will result in damage to the alarm, failure to operate, or a shock hazard.